Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
A vw3cantap2 (CAN Tap) is used to control an ATV31 from a PLC via CANopen. If Powersuite is connected to the Powersuite port. Which connection has write access to the drive. Do both connections have write and read access at the same time?
Causes and Fixes
If CANopen take the hand ( via CMDD ) it will not possible to control it by Powersuite, but it's always possible to modify some parameters depend on it ( motor stopped or not ). In fact and it's an example : if you adjust LSP via powersuite and also with CAN ( via PDO ) it will rewrite by the PDO because it's periodics.