Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
What minimum voltage is it possible to use ATV68, when switching-off protection undervoltage? Thank you very much for your help.
Facts and Changes
Causes and Fixes
400 V range = 287 V
500 V range = 346 V
690 V range = 537 V
If the control is supplied with an external source 24V, if the voltage goes under the guarantied range, and if the fault undervoltage is deactivated (E3.08), the drive is going to supply the motor in downgraded operation (speed reduction, current limitation...) as long as no other fault appears.