Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
The purpose of this resolution is to inform the user about an unexpected Timeout behavior of the Quantum Output module 140 DDO 364 00.
Facts and Changes
Quantum Output modules default in case of Timeout of communication to a PLC in general is Set to Zero.
Due to an incorrect default parameter of the 140 DDO 364 00, the Timeout behavior is Hold Last Value.
Affected Concept versions: Concept 2.2
To change the Timeout behavior, the user has to open the Module Parameter screen and has to leave it by the OK button. To leave it by the Cancel button will not change the Timeout behavior.
Causes and Fixes
The Timeout default will be corrected with Concept 2.6SR2
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!