Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
A ATV58FHU90N4 applied for a tension control application. The 3 phase current at output side is at balance( 6.96A, 6.99A, 6.99A). However, its current at input side is not in balance(4.0A, 4.0A, 4.7A). The input voltage for ATV58FHU90N4 is in balance. The customer put a line choke in front of this ATV58FHU90N4. Why the input current is not in balance? - - -> The ATV58FHU90N4 is a new and good drive. For a long term consideration, will this unbalance input current destroy diode bridge of ATV58F?
Causes and Fixes
Possible reasons for unbalance :
- bad connections
- line impedance
- transfomer coupling
- IT neutral
For a long terme there is no problem for the inverter.