Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
A customer will connect several motors in parallel for conveyor application, and they will be driven by a ATV68C23N4. However, the total motors' rating current is less than ATV68C23N4's current. How to setup the motor data in Menu B3 for this case? Is there any particular parameter setting need to be configured for this motor parallel case?
Causes and Fixes
For this application there is some restrictions :
- need to have same motors
- same cabe lenght for each motor
However, for the B3 menu :
B3.00 = global power ( sum of motors )
B3.01 = global current
B3.02 = nominal voltage
B3.03 = nominal frequency
B3.04 = nominal speed
B3.05 = nominal network voltage
And make a tune only if you have exactly same motors.