Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A -201 PLC out of Memory may be due to memory fragmentation.
- Adjust the global data size. A Memory Prediction should tell the user what percentage of
the Global data size configured is actually used. This number may be decreased (found in PLC Configuration).
Memory prediction will also indicate how much of the allocated memory has been used.
This may indicate that a larger PLC is needed.
- Increase heap size in the PLC configuration. If no 984LL is used, the heap size may be pushed to the maximum.
- Optimize the project.
- Perform a complete download it has not been done recently.
- Optimize the usage of coils and contacts both in range and usage.
- Adjust program data area
- Delete unused variables in Variable editor.
- You may have to choose a larger PLC.