Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The high byte of fifth configuration register for the MBP_MSTR block is used to define which backplane slot position the Ethernet module resides in.
The older Quantum controllers had a single slot Ethernet head module so the high byte of that register would be set to the slot number in which the NOE resides.