Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The ATV31 does not have Pull Up / Pull Down resistors for the RS485 Modbus communication. Have you seen any SLF when cables are disconnected? Do you recommend external resistors to maintain the proper bias?
Facts and Changes
ATV31 Modbus RS485
Causes and Fixes
The Pull up / Pull down are not present on the RS485 interface, but there is some confusion. In fact there is a time out if you take the hand on ATV31 bthe CMD word and if there is cab disconnection, the inverter will trip in SLF. It's not the case if you modbus only to read or write some parameters.