Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
What is the derating factor used when sizing LH4N for a high number of starts per hour than the standard spec of 360 seconds.
Facts and Changes
Causes and Fixes
There is not studies which gives a factor to determine the power of LH4 in an appliction with high number start/stop per hour upper her electrical characteristics of the product.
The catalogue tell you :
-'' if starting and stpopping conditions are severe, or if the starting current must be controlled, it is preferable to use an ATS48 unit''.
- ''beyond this starting duty, the start unit must be derated by one size''.
However , we thinks when the number of start/stop is considerable and it would have been preferable to use a variable speed drive.
Note: The LH4 softstart family is obsolete. It was replaced by the ATS01 softstart, or in the case of the larger LH4's the ATS22.