Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
By default, both channels support three-wire IEC Pt100 RTD APS_SENSORS.
If the sensor is not connected to the channel, the module will detect a broken wire and flash an error on the LED
By using the Advantys Config Tool:
You may change the input sensor type on a per/channel basis to be one of several types of TC, mV, or RTD devices.
If you are not using a sensor on one of the channels, you may configure it as type "none".
Note: Broken wire detection is not provided for mV APS_SENSORS.