The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
communcation on Modbus with aTS46 We have a site comprising several ATS46s communicating with TSX Premium master. The communication protocol is unitelway.But one of the ATS46s has failed and we have to replace it by a ATS48.But ATS48s only communicate via modbus which means that we need to change communication protocol of other ATS46s with modbus.So,my question is,how can we change the com. protocol of ATS46 from unitelway to modbus?Do we need the ATS software or the panel is sufficient? Or does it recognize the protocol automatically? Best Regards,
Facts and Changes
communcation on Modbus with ATS46
Causes and Fixes
For that you need to have the VW3G46301 option ( normally you have it ) and a PC with Terminal emulation software ( TTY ), included in Windows and also the cable for ATS PC Software and send special request to the ATS, complete procedure in the user's manual page 69 but the best way is to use the PC software ( more simple ). Concerning the physical layer, it's the same.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!