Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
What is the suitable action to replace the an ATV66FC10N4 with the new ATV68FC10N4? you have to note the following:
1-ATV 66 is connected to a PLC with fipway communication
2-how the maintaining on the panel will be
3-the motor was the old one come with ATV66 ,will we make any modifications? the big issue is the communication between drive and PLC as this ATV68 will be spare now and must be ready to be installed at any time
Facts and Changes
Causes and Fixes
Concerning the communication with Fipio you need to add a gateway, VW3A68301 ( you can download the documentation on Intranet at the Shopping kiosk ) , after you need to configure the ATV68 following the application, be careful there is no complete messaging capacity.
No problem for the ATV68 choice. Mechanically these inverters are completly different and you need to adapt some parts ( cables and so on ...).
For the encoder, it's the same ( RS422 - 5v ). Normally it's not necessary to modify the motor.