The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
What is the suitable action to replace the an ATV66FC10N4 with the new ATV68FC10N4? you have to note the following:
1-ATV 66 is connected to a PLC with fipway communication
2-how the maintaining on the panel will be
3-the motor was the old one come with ATV66 ,will we make any modifications? the big issue is the communication between drive and PLC as this ATV68 will be spare now and must be ready to be installed at any time
Facts and Changes
Causes and Fixes
Concerning the communication with Fipio you need to add a gateway, VW3A68301 ( you can download the documentation on Intranet at the Shopping kiosk ) , after you need to configure the ATV68 following the application, be careful there is no complete messaging capacity.
No problem for the ATV68 choice. Mechanically these inverters are completly different and you need to adapt some parts ( cables and so on ...).
For the encoder, it's the same ( RS422 - 5v ). Normally it's not necessary to modify the motor.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!