Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
ATV28 replaced by an ATV11. Speed point come from a PLC ( analog output ).
Probelm: there is no really 0v but 0,2 or 0,3v. At this value the ATV11 running , not the ATV28.
Causes and Fixes
The solution is to put a diode or choose an ATV11 with S315 specification. This version have CrL and CrH functionnalities, like the ATV58