Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
In ATV66 I have found the following programing. By Pass: YES Start Input: LI4 CD contact output: R2 Delay Time: 0,2 Sequence Tof: 5 Proccess Tof: 60 We will supply him with an ATV58.Is the programming above relative with the "downstream contactor control" with R2 relay in ATV58.And if it is not, what must we program in ATV58 to have the same result
Causes and Fixes
The Bypass is equal to downstream contactor but is not possible to adjust the temporisation, if you need this function , please use ATV68.