Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
You should find that a WinConX folder is created and placed on your windows desktop upon installation of the Modbus Plus driver. You will find utilities in both the MBX Driver and Virtual MBX Driver folders called MBX Demo and MBP Stat. These utilities will allow users to test for both general network errors and specific node errors. A volt ohmmeter can be used for checking cable continuity. Another common tool for troubleshooting networks is a Time Domain Reflectometer (TDR). This electronic instrument is used to find opens, short circuits, splices, taps, water ingress and other more elusive impedance mismatches.