Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
After powering display module, it got "freeze" showing this message: ..lnl. No more message after that message.It happened with (03) display modules. Our customer is trying to communicate the ATV58 to TSX Momentum in MODBUS protocol. See attachments
Facts and Changes
Reference: VW3A58101 V52IE27 (02)G0244, (01) G0241. We replaced one of them with an other display serial:G0003 and this display didn't have any problem. I downloaded the setting from ATV58 with powersuite, tbr=19200bauds. It means that baud rate of the RS485 serial link hasn't been changed. What could be the problem?
Causes and Fixes
This problem is in analysis and it concern the keypad EEPROM, it's a quality problem. For the moment the only solution is to replace the faulty keypad by 03 manufactured datecode.