The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
After powering display module, it got "freeze" showing this message: ..lnl. No more message after that message.It happened with (03) display modules. Our customer is trying to communicate the ATV58 to TSX Momentum in MODBUS protocol. See attachments
Facts and Changes
Reference: VW3A58101 V52IE27 (02)G0244, (01) G0241. We replaced one of them with an other display serial:G0003 and this display didn't have any problem. I downloaded the setting from ATV58 with powersuite, tbr=19200bauds. It means that baud rate of the RS485 serial link hasn't been changed. What could be the problem?
Causes and Fixes
This problem is in analysis and it concern the keypad EEPROM, it's a quality problem. For the moment the only solution is to replace the faulty keypad by 03 manufactured datecode.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!