Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, word 2 of the MSTR Instruction Function Code #3 (Get Local Statistics) will give you the Modbus Plus Network address of the PLC.
Below is a example of a MSTR Instruction using Function Code #3 (Get Local Statistics) to get the Modbus Plus address of the PLC
400001 = 3 (Operation Type)
400003 = 1 (length)
400004 = 2 (Offset)
400010 = 2 (Network address of this station)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!