The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
1. The wiring method of Modbus car / LonWorks module. How to connect with twisted pair cable w/o connector ?
2. Display parameters of VVD :- P-P or P-N output voltage show ? 3 the power consumed shown is motor power or VVD power ?
4 the running hours shown is accumlated or reset after power off ?
Facts and Changes
Drives are used in Building for HVAC application
Causes and Fixes
1- it's not possible the gateway w/o connector, one RJ45 for the modbus slave and one 5 terminals ( screw ) for the Lonworks.
2 - What do you mean by - P-P or P-N output voltage show ?
3 - APH, power consumed is for the motor
4 - The running hours ( RPR ) is accumulated but you need v5.2 ie37 control board to reset it and only for the inverter.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!