Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
1. The wiring method of Modbus car / LonWorks module. How to connect with twisted pair cable w/o connector ?
2. Display parameters of VVD :- P-P or P-N output voltage show ? 3 the power consumed shown is motor power or VVD power ?
4 the running hours shown is accumlated or reset after power off ?
Facts and Changes
Drives are used in Building for HVAC application
Causes and Fixes
1- it's not possible the gateway w/o connector, one RJ45 for the modbus slave and one 5 terminals ( screw ) for the Lonworks.
2 - What do you mean by - P-P or P-N output voltage show ?
3 - APH, power consumed is for the motor
4 - The running hours ( RPR ) is accumulated but you need v5.2 ie37 control board to reset it and only for the inverter.