Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
ATV28 trips with SCF, driving a submerged pump. ATV38 runs without any problem in the same case!
Facts and Changes
ATV28 submerged pump we often have this problems with ATV28
Causes and Fixes
This fault is detected by the ZCT (zero current transformer).
Trip level is a differential current > 2.5 A
But if there is a 2.5A leakage current (or unbalance between phase)
So we advise to check the earth and unbalanced current with an oscilloscope at the moment of the fault.
If the cable is shielded check that it is correctly connect (no high current circulation in the shield).
Test with disconnecting one side of the shield.
Test with a motor inductance (may be the capacitance of cable and motor is high and generate leak current peak.
Check that the supply voltage is stable and at the good value when the fault occurs.
Concerning the ATV38, it's not similar process.