Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
ATV68C13N4 central board has failed. This is the second one to fail in 1 week. The VSD was powered up but NOT running. The cooling fans stopeed and the display went blank.
Facts and Changes
Causes and Fixes
We have had quality problems with some diodes on this case ( they were put in short circuit ), the stock in Evreus has been replace in beginning of June.