Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The "invalid configuration: Company ID invalid" error when trying to download a application to a Panelmate is caused due to a software incompatibility between the Panelmate and the Panelmate Configuration software being used. Modicon Plus series Panelmates are only compatible with Modicon Panelmate software. IDT EATON Power series Panelmates are only compatible with IDT Eaton software. If a user attempts to mismatch the software to the hardware, this error occurs. The Company ID is displayed on the system page which is accessible in a Panelmate while in Off-Line mode.