Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Schindler Elevator (from Vienna, Austria) wants to start and stop the ATS48 by means of a contact on the isolation contactor. They did this with the ATS46 with no fault. Now, the ATS48 gives PHF. What is the solution?
Until they have a solution, they will continue to use the ATS46. If we have no more ATS46, they will use a competitor's soft start.
Causes and Fixes
The PHF detection on the ATS48 is not the same like the ATS46.
ATS46: undervoltage on phases.
phases unbalance during 500 msec and
Absence of the three phases network simultaneously during 200 ms with the starting order.
In your case, the sequence is not standard but check the version of your starter , the PHF detection was improved since the version 1.1 ie09.
In your sequence you can use the R1 relay for the insulation contactor.