Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Is it possible to connect the PC with Powersuite to the RS485 on the VW3A58303 and NOT to the RS485 on the control board?
The customer needs the displays and the connection to Powersuite at the same time.
I made some tests and it is impossible to get a connection with the option board. In Powersuite I used connection to ATV with bus-system and the correct ModBus address.
Parameters from the Menu 8: MB RTU, 19200, 8n1.
With the internal RS485 it works well.
Causes and Fixes
It's not possible to use PowerSuite on the Modbus card because at the first step connection of PowerSuite, there is an identification request and this one is not recognized by the option card.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!