Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, Symax Remote I/O will operate in a Quantum Hot Standby system. To connect the Symax I/O to the Quantum RI/O network a CRM931 Remote I/O interface is required and the I/O must be configured in the Application I/O map.
NOTE: All 8030 RIM125 must be updated to 8030 RIM125S if used in current loop mode.
Hold up time default is 3 ms and must be changed to 4 ms.