Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Yes, Symax Remote I/O will operate in a Quantum Hot Standby system. To connect the Symax I/O to the Quantum RI/O network a CRM931 Remote I/O interface is required and the I/O must be configured in the Application I/O map.
NOTE: All 8030 RIM125 must be updated to 8030 RIM125S if used in current loop mode.
Hold up time default is 3 ms and must be changed to 4 ms.