Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Version mismatch error is caused when project files become out of synch. This happens when a project is exported and imported on another PC. The export process does a code optimization thus resetting time and date stamp information in the .dsk file. This was an issue in Concept versions prior to 2.5. A workaround was to copy the complete project file from the source PC to the target PC. Concept 2.5 resolved the issue by adding an option to the Converter export process,
Export >> Project with used DFBs ( Re-Connect to Equal ).