The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Version mismatch error is caused when project files become out of synch. This happens when a project is exported and imported on another PC. The export process does a code optimization thus resetting time and date stamp information in the .dsk file. This was an issue in Concept versions prior to 2.5. A workaround was to copy the complete project file from the source PC to the target PC. Concept 2.5 resolved the issue by adding an option to the Converter export process,
Export >> Project with used DFBs ( Re-Connect to Equal ).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!