Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
When a yellow warning triangle is displayed in Concept it usually occurs when opening a section of IEC LD.
The source of the warning fault is a vertical or horizontal short has been placed on top of an existing
short. The logic is not affected and will execute as designed. The problem can be corrected by performing
a 'select all' on the section, cutting and then pasting the logic back into the section.