Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The OURBUS error is an indication of a mismatch between the I/O modules in the rack and the I/O map (Traffic cop) configuration.
First, check the interface module (J89x/ P89x) for the proper address settings.
Then view the I/O map (Traffic cop) for that particular drop.
The modules entered in the I/O map (Traffic cop) must match those physically in the rack.
Each module must have a green Active light.
Any modules that are missing from the rack or do not have "Active" lights will produce an OURBUS error on the interface module.