Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
On HMISTU655 PV:02, RL:01 SV:1.0, it is impossible to download application using USB Stick memory.
Causes and Fixes
We have published an IQ 102392 and recall the stock to update it in the manufacture plan. This new version PV:02, RL:02 SV:2.0 require to use a new software version. It is mandatory todownload the VJD5.1 SP1 and VJDSP1Hotfix1 from Schneider Live Update or Planet and install them on the PC