Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Yes, there are two possible solutions:
1. Using the local display (TWD XCPODC or TWD XCPODM).
2. System bits and words method: to use this method follow the sequence below:
- Set the system bit %S101 to 1
- Change the address values of the communication ports.
%SW101 for port 1
%SW102 for port 2
- Set the system bit %S101 to 0, at that time, the system will take into account the new addresses,
apply instantly the changes, and save the data into the configuration part of the application.