Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Differential protection stage in VAMP 265 is based on fundamental frequency phasors which are calculated using discrete Fourier transforms (DFT). The sampling rate is 32 samples per cycle and the DFT sampling window width is one cycle. The fundamental frequency current phasors are calculated every ten milliseconds.