Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
This error message indicated that the communications to the ADVC controller are not configured correctly. To configure these parameters, click options > Go Offline (it never went online but the software will continue trying until manually stopped) then click on Customize > WSOS Communications > Click the tab that described the method which you are using for communications and configure it accordingly. Most commonly this is Direct (Connecting directly to the front face of the ADVC controller) and the communications port needs to be selected (this may be confirmed from the Device Manger within the Windows operating system).