Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The Sepam digital relay's will have one of two connections available for a neutral CT or injection point. On Sepam relays with a CCA634 module terminals 7 and 8 will be used and secondary injection may be performed directly on the terminals. On Sepam digital relays with the CCA630 module, the only connections available are for the three line phases (A, B, and C) the neutral current must be brought to the Sepam relay via terminals 18 an 19 on the A terminal block. These terminals may not be directly injected as the signal must be converted using the CSH30, CSH120 or CSH200 module.