The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
The Sepam digital relay's will have one of two connections available for a neutral CT or injection point. On Sepam relays with a CCA634 module terminals 7 and 8 will be used and secondary injection may be performed directly on the terminals. On Sepam digital relays with the CCA630 module, the only connections available are for the three line phases (A, B, and C) the neutral current must be brought to the Sepam relay via terminals 18 an 19 on the A terminal block. These terminals may not be directly injected as the signal must be converted using the CSH30, CSH120 or CSH200 module.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!