Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
By default, when the ADVC controller enters the low power state the radio will be disabled after a programmable delay. To modify this setting such that the radio is not disabled, set the holdup time to 0. This may be modified from the front screen or via the WSOS software. To modify from within WSOS, open the switchgear file (or create it if necessary) click on Display > Radio Voltage > set the Holdup time to 0.