Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The global equation editor variables (form of V1, V2, V3, NOT VL1, VL2, etc) may be assigned to the output contacts on the Sepam relay. It is possible that outputs O1, O4, and/or O11 (for Sepam 40 series) or O1,O5, and/or O101 will be grey due to CB control being set to on. The only way to assign the global variable to one of these contacts is to turn CB control off.
Note: Setting CB Control to off will disable the Circuit Breaker Control functionality of the relay.