Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
O4 does not need to be wired for the SEPAM 20 and 40 series to provide proper protection. O4 is used as a watchdog only. O4 acts as a malfunction detection output such that if a fault occurs in the relay it will be detected. The relay will then open the circuit breaker and enter fault mode.