Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Get a fault on the SEPAM 40 series TC fault or TP phase fault but don't know what it means.
SEPAM 4x Series
"TC faults" and "TP phase faults" relate to Current Transformer Supervision (CTS) and Voltage Transformer Supervision (VTS), which can be set using the advanced UMI or SFT2841 software.
When enabled, the SEPAM relay will supervise the current and voltage APS_SENSORS and make sure that a phase isn't missing or a fuse isn't blown. The status of the CTS or VTS can be viewed via Modbus using TS indicators.
TC fault = CTS fault
TP Phase fault = VTS fault relating to phase difference between current and voltage
TP Vo fault = VTS fault relating to 3 phase voltage sum (Vr)