Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
When setting the ANSI 50/51N protection, the Sepam relay provides 2 different options for residual current type: "Sum 3I" and "Input Io".
The residual current type depends on the wiring of the current APS_SENSORS to the relay. If, for example, the relay is wired with a standard 3-phase current connection without wiring the Ir input of the CCA634 or using a CSH zero-sequence ct, the "Sum 3I" option needs to be selected. The measurement of the 3-phase currents allows the "calculation" of residual current.
* Note: A 2-phase current connection will not calculate residual current.
If, for example, the CCA634 Ir input is wired or a CSH zero-sequence ct is used, the Sepam will "measure" the residual current and "Input Io" needs to be selected when configuring 50/51N.