Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The ANSI 50/51 protection option in SEPAM relays combine both ANSI 50 instantaneous phase overcurrent protection and ANSI 51 delayed phase overcurrent protection.
In order to activate ANSI 50 protection, an instantaneous delay of 50ms must be set for the time delay. This is the lowest response time of the relay to a short-circuit fault. This includes Operating time + Overshoot time.
In order to activate ANSI 51 protection, a delay greater than 50ms must be set for the same parameter setting time delay. This will allow the end-user to use ANSI 51 delayed phase overcurrent protection.