Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
For Sepam 80: what is the correct order for adding the accessories MSA 141, MET 148, DSM 303, and MCS 025?
Causes and Fixes
The Sepam 80 has got 2 Ports. Using these, it is always possible to be able add all the different accessories that one might need for the Sepam 80.
On the D1 port, connect in order the MSA 141, next 1 or 2 MET 148 ( 1 MET 148 if you use also DSM 303) and next at the end the DSM 303
On the D2 port, connect in order the Second MET 148 and the MCS 025 at the end.
You can connect a maximum of three accessories on each port (D1 or D2).
The DSM 303 and the MCS 025 have to be always at the end of this chain. So if you use these 2 Accessories DSM and MCS on same Sepam 80, you have to use necessarily the 2 ports ( i.e. set the DSM at the end of D1 and set the MCS 025 at the end of D2)