Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
What is the right way to connect and chain the MET 148, MSA 141, and DSM 303 accessories on the Sepam 20 or 40?
Causes and Fixes
On the D Port you have to connect and chain in order:
(1) MSA 141
(2) MET 148 ( Attention: Option 2 MET 148 for Sepam 40 only )
(3) DSM 303 (Always at the end of this chain and only if no more than 2 accessories already connected on Sepam)
Note: you can't connect more 3 accessories on this chain so if you already have 1 MSA 141 and 2 MET 148 it is impossible to set also 1 DSM 303. In this case if you want to put this DSM 303, you have to remove the MSA 141 or 1 MET 148.
Key words and phrases: MSA141, MET148, DSM303