Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
VIGI PA: can we use the MITOP Output of the EPAMI MI 321 for the self-tripping of the MC SET circuit breaker?
Causes and Fixes
Yes we can with the old generation of MC SET 4 (with GMH order like the 24 KV) because the MITOP is more sensitive than the new MITOP of MC 500 (not yet approved by EDF).