Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
If you have a problem as per below, you need to check 2 things.
a. The hard-wired signals from the CB which are for CB On/Off status must be connected to Sepam 40 following the default IO setting. (Please take a Sepam 40 manual for more details.)
b. Device closed tag must be added into your project.
You can find this tag under Sepam Series 40 with default IO device type -> Miscellaneous -> Real Time Tags in PowerLogic SCADA Profile Editor.
Check also last Updated information from our PowerLogic L3 Team
Key words and phrases:
question mark, meaning, signification, signify, mean, what
Original Author: YJ
All content © 1992-2009 Schneider Electric