Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
If you have a problem as per below, you need to check 2 things.
a. The hard-wired signals from the CB which are for CB On/Off status must be connected to Sepam 40 following the default IO setting. (Please take a Sepam 40 manual for more details.)
b. Device closed tag must be added into your project.
You can find this tag under Sepam Series 40 with default IO device type -> Miscellaneous -> Real Time Tags in PowerLogic SCADA Profile Editor.
Check also last Updated information from our PowerLogic L3 Team
Key words and phrases:
question mark, meaning, signification, signify, mean, what
Original Author: YJ
All content © 1992-2009 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!