Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
For the Sepam Series 20 and 40 relay, "remote control" can be activated by navigating through the front face of the Sepam relay.
Go to general settings -> Modules -> Modbus. Scroll down until the remote control screen appears.
Note: "SBO" means Select Before Operate
For the Sepam Series 60 and 80 relay, "remote control" cannot be activated by navigating through the front face.
In order to activate this setting, connect to the relay using the SFT2841 Software kit with the CCA783 cord.
"Remote Settings" is located under the "General Characteristics" tab of SFT2841.
Date Created: March 13, 2008
Last Revised: October 21, 2008
Original Author: JJ
All content © 1992-2008 Schneider Electric