The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
If the green led stays lit on the ACE9xx module that means there is a comms wiring issue. For normal working conditions, the green light would be:
a) turned off when Stand-By i.e. Commubnication frame to SCADA
b) flickering when communicating to SCADA
In order to fix the wiring issue, verify:
a) That the module is not grounded more than once. Often, the shield is exposed and grounded unnecessarily with the clamp, which is located below the terminals. Make sure that the shield isn't exposed and touching this clamp.
b) That the RS485 terminals are wired correctly. Here are the wiring diagrams for 2-wire and 4-wire communication:
For 2 wires:
Warning: L+ connects to L- and vise-versa when communicating to a powerlogic or third-party device on the same daisy chain!!!!
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!