Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The active green LED must be on in order to communicate to the MSA141 or MET148-2 remote modules. The active green LED means that the module is powered and receiving control power from the Sepam relay. If the green LED is OFF, verify that the CCA77x cable is wired correctly from the "D" port of the Sepam to the "Da" port of the remote module. Also, verify that the Sepam relay is energized, or else the remote module will not receive the power from the Sepam relay.
Date Created: March 4, 2008
Last Revised: September 13, 2008
Original Author: JJ
All content © 1992-2008 Schneider Electric