Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A current transformer (1A or 5A) is attached to the rear panel of a Sepam relay via the the CCA630 connector. The CCA630 connector can
connect three current transformers to a Sepam relay.
The CCA630 connector contains interposing ring current transformers (CT) with through primaries. When measuring phase and zero sequence currents, these primaries provide impedance matching and isolation between the 1A or 5A circuits and the Sepam relay.