The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Most likely what has happened is that the value being inputted to the Modbus slave module has overloaded the 16bit register. The kWd value inside the meter is a floating point value, while communications is 16 bits. The default Modbus register scaling is (x1) for Power Parameters (PPS register sets the scaling).
To eliminate the problem you may need to change the PPS scaling registers from the default (x1) value to a more appropriate value related to the system.
i.e.: by changing the value to 0.001, you will effectively be dividing the kWd value by 1000 for transmission in the Modbus register.
See Step 9 (page 18) for information on programming PPS scaling on the ION 6200 meter.
Last Revised: June 22 2007
All content © 1992-2007 Schneider Electric
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!