Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Most likely what has happened is that the value being inputted to the Modbus slave module has overloaded the 16bit register. The kWd value inside the meter is a floating point value, while communications is 16 bits. The default Modbus register scaling is (x1) for Power Parameters (PPS register sets the scaling).
To eliminate the problem you may need to change the PPS scaling registers from the default (x1) value to a more appropriate value related to the system.
i.e.: by changing the value to 0.001, you will effectively be dividing the kWd value by 1000 for transmission in the Modbus register.
See Step 9 (page 18) for information on programming PPS scaling on the ION 6200 meter.
Last Revised: June 22 2007
All content © 1992-2007 Schneider Electric