Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Effects of interruptions of the DC power supply. (CEI60255-11)
The effects are determined for an interruption with a duration chosen in the following list and declared by the manufacturer : 2 _ 5 _10 _ 20 _ 50 _ 100 _ 200 ms
The interruption must be sudden, i.e.the auxiliary power supply must vary from 0 to the rated value and the opposite .
The relay must not change erroneously its output status when the power supply value is applied or cancelled.
Fugitive cancellings Sepam 1000+ S20: 10ms.
Fugitive cancellings Sepam 1000+ S40: 20ms.
Fugitive cancellings Sepam Series 80: 100ms
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 20, 40, and 80
All content © 1992-2008 Schneider Electric