Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Effects of interruptions of the DC power supply. (IEC 60255-11)
The effects are determined for an interruption with a duration chosen in the following list and declared by the manufacturer : 2 _ 5 _10 _ 20 _ 50 _ 100 _ 200 ms
The interruption must be sudden, i.e.the auxiliary power supply must vary from 0 to the rated value and the opposite .
The relay must not change erroneously its output status when the power supply value is applied or cancelled.
Fugitive cancellings Sepam 2000:
75 ms to Vsupply = Vnominal
30 ms to Vsupply = Vmini
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 2000
All content © 1992-2008 Schneider Electric