Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
With the Modbus communication link, remote control orders such as opening and closing of the breaking device or activation/inhibition of Sepam functions can be transmitted to Sepam 1000+.
The remote control orders may be carried out in 2 modes:
- direct mode: the remote control order is effective as soon as it is received
- SBO, Select Before Operate mode: the remote control order is executed in 2 steps, after reception by Sepam of 2 coherent orders, first the selection order and then the execution order.
The SBO mode is safer.
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 1000+ (Sepam Series 20 and Sepam Series 40)
Original Author: FK
All content © 1992-2008 Schneider Electric