Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
With the Modbus communication link, remote control orders such as opening and closing of the breaking device or activation/inhibition of Sepam functions can be transmitted to Sepam 1000+.
The remote control orders may be carried out in 2 modes:
- direct mode: the remote control order is effective as soon as it is received
- SBO, Select Before Operate mode: the remote control order is executed in 2 steps, after reception by Sepam of 2 coherent orders, first the selection order and then the execution order.
The SBO mode is safer.
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 1000+ (Sepam Series 20 and Sepam Series 40)
Original Author: FK
All content © 1992-2008 Schneider Electric